EASERGY T200 PDF
MV electrical network management MV substation control unit Merlin Gerin Easergy range Easergy T I User’s manual Easergy T I Contents Overview . Download: Easergy T P (series 3) User’s manual – Easergy TP. Easergy T I user manual – Schneider Electric. ic. dk. Views. 4 years ago. Module, · Enclosure, · Automation, · Interface.
|Published (Last):||15 April 2012|
|PDF File Size:||10.6 Mb|
|ePub File Size:||8.16 Mb|
|Price:||Free* [*Free Regsitration Required]|
The automation locks if an error is detected during a changeover sequence one switch opens and the other closes.
It is combined with VD3H voltage detectors. Earthing d The equipment must be earthed to ensure E. The principle is to open all the switches when voltage is lost and to progressively restore power to the network by successively closing the switches.
Easergy T200 P – Schneider Electric
T P changes to the other channel when there is a fault on the active channel v automatic return: Schneider Electric Design, production: It manages the functions of 1 to 4 switches and controls local operation, with the exception of communications.
Check the charger and the batteries.
Measurement acquisition and processing The T P can incorporate the following measurements and processing functions for each channel: The time before sending an alarm is defined randomly between the min. DE Switching on the AC supply b Close the safety fuse inside the enclosure see illustration opposite.
PE Compact enclosure The equipment is housed in a stainless steel enclosure, ensuring: The T is capable of storing two different software versions in memory.
Use of an external fault detector with a fault reset output. Protected by a 0. A battery fault alarm informs the remote control system of an imminent discharge. It is a 5 x 20 mm, 5 A time-lag fuse. The Power supply module is used to reset the power supply: The HTML pages are refreshed in real time every three seconds so as to update the states reported by the T It ranges from to bauds.
Incoming voltage 1 Operating modes b The operating mode is selected from the Easergy T configurator. T must detect a fault current confirmed by the loss of the T supply voltage MV before the SEC automation can give this opening order it must therefore be equipped with this function. For all the logs, when the storage capacity is reached, the most recent event occurring erases the oldest event on the list.
Documents Flashcards Grammar checker. Locking the source transfer A digital input prevents the transmission of orders from the control panel, the automation and the remote control station. DE Switch control 1 2 3 4 Way 1 to 4 selection The switches can only be controlled via the Control module if: The advantages of this type of battery include the fact that there is no risk of explosion, no acid leakage and no servicing requirement.
Upon reception, wait before sending the response to avoid overlapping Request To Send. EE2 Resistance Ohms Law.
Easergy T I – Schneider Electric
Documents Flashcards Grammar checker. The shields must be earthed at one point in the line preferably on the PC side of the remote control station. When installing the enclosure on the column, make sure not to conceal the air vent inlets so as to enable good circulation of air. The variable types that can be used are the same as for PLC programmes existing variables or virtual variables eaxergy specifically.
Voltage measurement Voltage loss detection Automation systems Current measurement Fault current detection Fault current detection Automation systems Phase-to-phase and phase-to-earth fault current detector: SW1 current 2 — Blanking plate: It can be used to eaesrgy the status of the equipment, time-stamped events and communications sent over the internal Modbus link.
Its main constituent parts are: The enclosure is held in position by the mounting bracket and can be released.
The date and time are only used for dating-stamped events and by the protocol analyser. The enclosure can be padlocked. It is accessible after removing the control panel front of the Control module. Otherwise, reset the Power supply module to trigger a battery test, after connecting battery to the rack; if the problem recurs after charging for 24 hours, replace the batteries.
The standard voltage of the internal power supply is 48 V although 24 V is possible on option.
Remote network control can be set up in phases by installing simple systems which provide a rapid return on capital and can be implemented in a few months.
RS Modbus local network Management of 3 virtual IP addresses or ethernet port Management of the various transmission modes The ports can be configured to be used with single or redundant channels: Battery autonomy b Duration: